RCD, RCCB & RCBO
This area is here for information purposes. Designers and installers should obtain their own copy of BS7671:2018 and follow the requirements and recommendations in the 18th Edition of the IET Wiring Regulations.
Order your copy here.
“For protection against electric shock”
What are RCDs?
RCDs is a generic term and it is commonly used to refer to devices such as RCCBs, RCBOs and other types of earth leakage detection operated protective devices.
What does the regulations say?
The use of RCDs particularly 30mA devices has been extended to include more applications and more types of installation in consecutive additions of the wiring regulations. For example 18th Edition requires all luminaire circuits in domestic household premises to be protected by 30mA RCD (411.3.4).
Consequently, greater emphasis is placed on protection against unwanted tripping of RCDs (see 531.3.2) and correct selection of the right type of RCD for each application. For example, in medical locations group 1 and 2, Type A or B are required.
What are my options?
Differing types of RCD are available; this section related to the various types.
For example reference is made to Type AC RCDs which are for general use.
Reference is also made to Type A, Type F & Type B RCDs which also detect pulsating DC residual current.
The appropriate type of RCD should be selected for each application, see 531.3.3.
- Type AC – General purpose use
- Type A – Where smooth DC to 6mA exists
- Type F – Where smooth DC to 10mA exists
- Type B – Where smooth DC to 0.4 times rated operating current, or 10mA, whichever is higher
This section is expanded considerably to aid designers with the selection of appropriate devices for particular applications.
Also Part 7 (section 722) includes specific requirements for EV Type A or B may be required and in Section 712 Solar photovoltaic (PV) power supply systems, Type B may be required.
How do I choose the right RCD?
The term RCD is used over 250 times in the 18th Edition of the Wiring Regulations.
To ensure that the correct type of RCD is selected the designer must match the operating characteristic of the RCD to the type of fault that can occur in the installation/equipment and manufacturer instructions should be consulted in the design and selection process.
What you need to know about RCDs and the 18th Edition
People talking about RCDs and the 18th Edition is, most of the time, a good thing, but occasionally it's a dangerous thing.
Discover more about RCDs and the 18th Edition in the piece below.
Get the 18th Edition Solution
Find out more about our RCD solutions to help you comply towards the 18th Edition below.
|Wylex||Consumer Units with 80A Type A RCDs||View here|
18th Edition on the Electrium Podcast
We talk the key questions from the 18th Edition on episode two of the Electrium Podcast.
This includes Arc Fault Detection Devices, Transient Overvoltage Protection, RCD Selection and more.
Getting the right 18th Edition solution for you
We have solutions to help you comply with the 18th Edition Wiring Regulations.
Our colleagues are based throughout the UK, and have local knowledge of your area. Chat with our team today and see how we can help you deliver your next project above and beyond your clients expectations.
Find a colleague in your local area here.
Get a 18th Edition solution in your area
Our 18th Edition solutions are available to you in your local area thanks to our network of wholesalers and stockists.
Use our 'Find a Stockist' service to discover your nearest supplier of 18th Edition products from our leading brands such as Crabtree and Wylex.
Find your 18th Edition solution here
Get the latest 18th Edition Info
Sign up to our newsletter and get all the latest information for our leading brands, including content on the 18th Edition of the Wiring Regulations.
Click here to sign up.
Putting the 'Social' in Social Media
Why not follow us on social media and let's continue the chat.
Just click, follow and enjoy.